WITH MEASURABLE RESULTS
HydraWrap® (Fiber Reinforced Polymer)
Water Treatment Plant
A section of piping that is immersed in a treatment tank had several deteriorated areas that required repair.
The solution utilized the HydraWrap® Structural Composite Repair System, as well as the HydraTite® NSF61 8001 Waterline Epoxy.
The customer requested that the pipe system be reinforced and brought back to its original design condition and that the repair be made in a very quick turnaround.
The HydraWrap® composite repair was designed to reinforce an 8″ diameter carbon steel supply pipe with a maximum design pressure of 90 psi. The design of the HydraWrap® was based on limiting the strain in the composite repair to the allowable strains recommended by ASME. After applying the HydraWrap® system to the pipe, the composite repair was top coated with HydraTech’s NSF61 8001 Waterline epoxy. The project took less than a week to perform.